What should I pay attention to when using a diesel generator in hot weather?
There are a lot of things that everyone needs to pay attention to during the use of diesel generator sets , so do you know enough to pay attention to using diesel generator sets when the weather is hot? Here are the details for everyone:
One, smooth smoke
The chamber must be opened through an outdoor exhaust pipe. The muffler must be ≥ the diameter of the smoke pipe. The pipe elbows must be connected to no more than 3 to ensure the smooth flow of exhaust gas. Injection; if installed vertically upwards on the exhaust pipe, the protective cover must be installed.
When concrete is used for the foundation, the level must be measured with a spirit level during the installation process so that the unit is fixed on the horizontal foundation. There should be special shock pads or foot bolts between the unit and the foundation.
Third, protective ground
The generator casing must be provided with a reliable protective ground. If you need a generator with a neutral point directly grounded, a professional should keep the neutral point grounded and configure a lightning protection device. It is strictly forbidden to use the mains grounding device for direct neutral grounding.
Fourth, good ventilation, avoid overheating
The installation site is well ventilated, the air inlet on the generator side is sufficient, and the air outlet on the diesel engine side is good. The area of the air outlet should be greater than 1.5 times the area of the water tank. Remember: Diesel generators should not be operated in high temperature environments under sunlight to prevent malfunctions caused by excessive temperature rise of the generator body.
Five, keep clean
The perimeter of the installation site should be kept clean to avoid placing objects near corrosive gases and steam that generates acids, alkalis, etc. A fire extinguishing device is better set.
Six, two-way switch
The two-way switch of the generator and the power supply must be very reliable in the case of reversed power transmission. The reliability of the two-way patch cord and inspection approved by the local power department. Check the approval of the local power supply department.