What are the causes of diesel generator start failure?
There will be failures during the use of diesel generator sets, so do you know the causes of diesel generator set startup failures? Let me introduce them in detail below:
1. Check whether the key switch of the diesel generator set works normally and whether there is output at the module start port.
2. Check whether the diesel generator set has a fault indication, repair the fault if necessary, and reset the corresponding fault information.
3. Check the battery voltage of the diesel generator set. If the voltage is too low, recharge the battery. If the voltage is normal, check whether the voltage signal is sent to each control link step by step according to the drawing, such as throttle solenoid valve, starter motor, etc.
4. Check whether the emergency stop button of the diesel generator set is released.
5. Whether the starting relay is good.
Next: No morereturn